The energy storage system consists of a 30-foot energy storage system container with a planned design capacity of 500kW/1MWh. The energy storage system container includes energy storage system, battery management system, PCS, UPS, EMS, lighting, fire protection, HVAC and distribution. Auxiliary components such as electrical access systems, with installation/maintenance channels;
The power grid system of the plant is connected to the power grid system of the power distribution room through the feeder cabinet to realize the functions of peak shaving and valley filling, demand management, energy saving, load balancing, dynamic capacity increase, and power factor improvement. The electrical topology of the energy storage system is as follows
OEM/ODM professional battery manufacturing factory, installed in place, convenient and quick
One-stop solution for customized energy storage system integration
Diversified customer needs, applicable to multiple scenarios
Intelligent operation and maintenance backstage, can view the system status, and easily obtain information
1 Peak shaving and valley filling, by charging and storing energy during the valley, and discharging energy during peak hours, reducing the electricity cost of enterprises or parks, and saving customers electricity costs
2 Demand response. When the short-term power consumption is greater than the capacity of the transformer, the energy storage system performs rapid discharge to meet the demand for electrical energy of the load.
3 Dynamic capacity increase, use energy storage equipment to replace the capacity of the voltage transformer at peak time, help users reduce the cost of transformer use, reduce transformer investment and expansion cycles, and conduct short-term power transactions on the power market trading platform in combination with load forecasts to maximize revenue.
4 Off-grid backup power supply provides an uninterrupted short-term power supply for important loads when the power is interrupted, reducing the economic loss caused by the sudden power failure of the load.
Solar Installed Capacity：350kW
Equivalent Full Hair Time：4-5h
Wind Power Installed Capacity：120kW
Monthly Electricity Consumption：70000kWh
Peak Load Power：120-150kW
Battery Cell：LifePO4 3.2V105Ah；
Battery Cluster(2P192S)：12pcs PACK，614.4V,210Ah,129.024kWh；
Battery System(2P192S*8)：614.4,400Ah, 129.024kWh*8=1032.192kWh;
Whole Cabin Capacity：1032.192kWh*2=2064.384kWh
Tell us your